Have a question or want to start a discussion? Post it! No Registration Necessary. Now with pictures!
- John White
September 9, 2009, 10:48 pm
rate this thread
5 out of 5
5 out of 5
In my main telcom room, I have a cabinet with a patch panel that was
pre-wired to a patch panel in my main data rack. I'm unclear about
the proper EIA/TIA 606-A labeling standards as applied to this
Do I consider the cabinet a different Telecommunications Space (TS)
from the cabinet?
Do I label the patch panel in the cabinet identically to the panel in
the main rack or just indicate in TS documentation that the two panels
Should I treat this situation is as a work area outlet that happens to
be in the same room and a full patch panel in size?
- » FCC Holds that Fax Broadcasters are Solely Responsible for TCPA Violations When They Dece...
- — The site's Newest Thread. Posted in » General Telecommunications Forum
- » Strike 3 Saga: Turning BitTorrent Downloads Into A Copyright Infringement Settlement...
- — The site's Last Updated Thread. Posted in » General Telecommunications Forum